Last edit: 03/03/2023
On the 13th July 2021 a revision was published. Hereafter the main changes in requirements
- It is made clear that "Self-protected Combination Motor Controllers " can be used to protect motor circuits only. For all other Branch Circuit Protective Devices (or BCPD), UL 489 circuit breakers and Fuses in compliance with UL 248 shall be used. Section 31.1.4 was modified.
- Since a few years we are discussing whether the Nameplate Data must be on the outside of the panel or it can be on the inside. We finally reached a compromise: the Label (that contains important data like the panel FLC and the Panel SCCR) can be on the inside; however, if the panel is for Industrial Machineries, the label much be on the outside. Therefore, the standard remains alligned with NFPA 79 that requires Nameplate Data "shall be attached to the outside of the enclosure". At the same time, it is alligned with several UL standards that allows the label to be on the inside, like UL 508. Table 52.1 was modified accordingly.
- It was finally clarified NOTE "b" in Table 38.1: Ampacities of control circuit conductors. The note stated that wire sizes of 20 to 26 AWG could be used "only for connection of control circuits for electronic programmable input/output and static control (having no moving parts)". That "and" should have been an "or" in reality. Now the new note clarifies that wires up to AWG 26 can be used "for connection of electronic control input/output and control devices". We are now fully alligned with NFPA 79, articole 220.127.116.11: "Conductors installed within control enclosures shall not be smaller than 26 AWG".
- Air conditioners should be provided with an SCCR. That is the meaning of the statement in 26.1.1 that they "shall comply with the requirements for general construction and power circuits". If they do not have one, they must be installed on an isolated secondary of a control transformer. The control transformer reduces the fault current to a value that will not cause any safety issue with the enclosure air conditioner in case a short circuit occurs. The new languange extends the exception, in section 26.1.1, to Air Conditioners.
UL 508A: Industrial Control Panels UL 508A – July 2021 update UL 508A – August 2020 update UL 508A – April 2020 Update UL 508A – Sizing of Feeder Circuits UL 508A – 66.1 Enclosure Access UL 508A – Traditional Combination Starters in North America UL 508A – Definitions UL 508A – Ampacities of Conductors UL 508A – Branch Circuit Currents Appendix D: Bus Bar System UL 508A – Current Limiting Devices UL 508A – Control Circuits